Technology Reports of Kansai University (ISSN: 04532198) is a monthly peer-reviewed and open-access international Journal. It was first built in 1959 and officially in 1975 till now by kansai university, japan. The journal covers all sort of engineering topic, mathematics and physics. Technology Reports of Kansai University (TRKU) was closed access journal until 2017. After that TRKU became open access journal. TRKU is a scopus indexed journal and directly run by faculty of engineering, kansai university.
Technology Reports of Kansai University (ISSN: 04532198) is a peer-reviewed journal. The journal covers all sort of engineering topic as well as mathematics and physics. the journal's scopes are
in the following fields but not limited to:
Internet of Things (IoT) and Cloud computing are extremely distinct technologies which are by now playing an important role in our life. It is expected that adopting and using them would be more and more common, that makes them significant components for the Future Internet (FI).The upcoming internet-associated revolution is almost there with the existence of the IoT. IoT empowers connection and communications among tons of devices between themselves to exchange information, knowledge, and data that promotes the quality of our daily lives. Alternatively, appropriate, upon-request, and adaptable network access is provided by Cloud Computing, as a result, makes it possible to contribute computing resources which helps dynamic data be integrated from a variety of data sources. However, Cloud Computing and IoT in FI cannot be implemented without an abundance of issues and problems. In this research paper, we will be endeavoring to outline and put light on the prime and main concepts of the Cloud Computing and IoT
Evaporative cooling is a good alternative of refrigeration cooling systems. This system is environmentally friendly and consumes low electrical energy. However, this system has some disadvantages which is greatly affect on the performance of the system. One of these problems is the affected by external conditions (humidity) makes space uncomfortable and reduces the effectiveness of evaporative cooling. This paper will focus on overcome this problem and improving the performance of the system. An evaporative cooling system was combined with heat recovery and desiccant in order to improve the performance of the system in a humid condition. The unit was constructed and installed at University of Technology in Baghdad. The system includes ducting, desiccant bed, plate heat exchanger (heat recovery), centrifugal fans and heaters. This is accomplished through reducing the moisture imposed on the cooling unit, as a result of handling the latent load of air (by desiccant material). Three air flow rate of supply in desiccant were studied (0.48, 0.61, and 0.73 m³/s). Four regeneration air flow rate in desiccant were studied (0.15, 0.28, 0.49 and 0.59 m³/s). The results show adding the desiccant material and heat recovery system could improve the performance of the system by 106 % (in a humid condition W=20.86 g/kg)